There are several methods for measuring air tightness that may result in different values and sometimes quite different uncertainties. The two main approaches trade off bias and precision errors and thus result indifferent outcomes for accuracy and repeatability. To interpret results from the two approaches, various questions need to be addressed, such as the need to measure the flow exponent, the need to make both pressurization and depressurization measurements and the role of wind in determining the accuracy and precision of the results. This article used a large dataset of blower door measurements to reach the following conclusions. For most tests the pressure exponent should be measured but for wind speeds greater than 6 m/s a fixed pressure exponent reduces experimental error. The variability in reported pressure exponents is mostly due to changes in envelope leakage characteristics. It is preferable to test in both pressurization and depressurization modes due to significant differences between the results in these two modes.
Reducing Uncertainty in Air Tightness Measurements
Languages: English | Pages: 2 pp
38th AIVC Conference "Ventilating healthy low-energy buildings", Nottingham, UK, 13-14 September 2017