Submitted by Maria.Kapsalaki on Wed, 02/05/2020 - 17:02
Between 2017 and 2018, the Centre for Studies and Expertise on Risks, the Environment, Mobility and Planning (Cerema) organized an airtightness measurement campaign in 117 multi-family collective and single-family French dwellings. These dwellings were built before 2005, that is, before the release in 2005 of the fifth French thermal regulation for new dwellings, that was the first to introduce specific requirements for airtightness.
Submitted by Maria.Kapsalaki on Tue, 02/04/2020 - 13:14
Ventilation is critical in interpreting indoor air quality (IAQ), yet few IAQ assessments report ventilation rates; even when they do, the measurement method is often not fully described. Most ventilation assessments use a tracer gas test (TGT) to measure total air change rate. In a TGT, the indoor air is marked with an easily identifiable gas (tracer) so that the air change rate can be inferred by monitoring the tracer’s injection rate and concentration.
Submitted by Maria.Kapsalaki on Mon, 03/21/2016 - 11:06
The paper presents a numerical methodology to assess the natural ventilation. UrbaWind is an automatic computational fluid dynamics code. It was developed to model the wind in urban environments. The turbulence modelling, namely the dependence of turbulence length on the distance from wall, and the model constants were calibrated in order to reproduce with good agreements flow separation around buildings walls and pressure coefficient field on façades. Numerical results match well with the experiments: separation patterns and pressure field on walls in dense urban areas.
Submitted by Maria.Kapsalaki on Wed, 11/06/2013 - 09:38
The global requirement to dramatically reduce greenhouse gas emissions places an increased emphasis on reducing energy demand associated with dwellings. Where improved energy efficiency is in part achieved by tighter control of ventilation, there is potential for both positive and negative impacts on health from reduced air exchange in the indoor environment. Although increased air tightness may help improve indoor temperatures and reduce the ingress of pollutants from the external environment, it may increase concentrations of those from indoor sources.
Submitted by Maria.Kapsalaki on Mon, 10/28/2013 - 10:39
To clarify the indoor climate in Japanese college classrooms, an air-conditioned, mechanically ventilated classroom of a university was surveyed. Temperatures, humidity and carbon dioxide (CO2) concentration in winter and summer were measured before, during and after lessons. The airtightness of the room and the airflow rate of the ventilation system were also measured. In winter, at an outdoor air temperature around 0 ºC and with the thermostat temperature of the air conditioners set to 30 ºC, the vertical difference in room air temperature exceeded 10 ºC.
Mechanical ventilation may be necessary to provide adequate ventilation in new houses due to the relatively low rates of infiltration achieved in new construction. However, in hot and humid climates, increased ventilation may raise indoor humidity to an undesirable level. A study was undertaken by the Florida Solar Energy Center (FSEC) to evaluate the humidity effects of different mechanical ventilation strategies for such climates. The study was conducted in a new 141-m2 manufactured house sited at the FSEC campus.
A study to measure indoor concentrations and emission rates of volatile organic compounds (VOCs), including formaldehyde, was conducted in a new, unoccupied manufactured house installed at the National Institute of Standards and Technology (NIST) campus. The house was instrumented to continuously monitor indoor temperature and relative humidity, heating and air conditioning system operation, and outdoor weather. It also was equipped with an automated tracer gas injection and detection system to estimate air change rates every 2 h.
Existing technical recommendations and standards regarding natural ventilation in Portugalestablish one air change rate, ACH, in main rooms (bedrooms and living rooms) and fourACH in service rooms (kitchens and bathrooms).
A combined windcatcher and light pipe (SunCatcher) was installed in the building of theSchool of Construction Management and Engineering in the MSc Seminar Room (2N09).Monitoring of indoor environment in real weather conditions was conducted to evaluate theperformance of windcatchers in the room and to conduct occupant survey. External weatherconditions and internal indoor environment and air quality indicators were recorded. Thetracer gas decay method using SF6 was used to establish the air change rate for variousconditions.
This paper considers the predictions obtained using a recently developed ventilation parameter (VP) for evaluating the ventilation performance which combines the indices for indoor air quality and thermal comfort. This ventilation parameter is used to analyse the changes in ventilation performance with changes in the position of workstation in a room ventilated using mixing ventilation.