This paper outlines the extension of a CFD model using DBM modelling approach. Primarily adynamic CFD model is proposed for adiabatic ventilation system. At the inlet a step rise in temperature of the incoming air with steady flow rate is used for the CFD simulation and temperature responses at 36 monitoring locations were extracted. In the second stage, the inlet and the extracted temperature profiles were used to develop DBM models at individual locations. Finally the developed compact DBM model was used to construct model based predictive control algorithm.