Submitted by Maria.Kapsalaki on Wed, 01/29/2020 - 12:52
Buildings account for approximately 40 % of energy use in the European Union, as well as in the United States. In light of the European Energy performance of buildings directive, efforts are underway to reduce this energy use by targeting zero or nearly zero energy buildings. In such low energy buildings in cold climates, ventilation to ensure suitable indoor air quality is responsible for half or more of their energy use. The use of heat recovery and demand-controlled ventilation are potential solutions to reduce ventilation-related energy consumption.
Submitted by Maria.Kapsalaki on Tue, 01/28/2020 - 12:04
With increasing building airtightness, the design of an adequate ventilation system gains importance. The first generation of ventilation systems, based on continuous supply of the nominal airflow rate, are now being replaced by Demand Controlled Ventilation (DCV). These systems, often H2O and/or CO2 controlled, do not take into account the emissions of Volatile Organic Compounds (VOCs) to the indoor environment.
Submitted by Maria.Kapsalaki on Tue, 03/22/2016 - 12:17
In an extensive simulation study using a multi-zone airflow and contaminant transport calculation software (CONTAM) recommendations for the supply air rates for residential housing were derived as input for the revision of the Austrian standard ÖNORM H 6038 (2014). The floor plan, the occupancy and the contaminant and humidity sources are modelled to represent a typical Austrian housing situation. A humidity buffering model is also implemented. Based on common thresholds for CO2, relative humidity (r.h.) and TVOC the so-called relative threshold deviation is determined.
Submitted by Maria.Kapsalaki on Tue, 08/19/2014 - 10:16
Methods of manipulating building envelope wind pressure distributions for application in the natural ventilation of high-rise buildings are presented using computer simulation methods. CFD was used to simulate the external flow while the multi-zone method was used to compute the flow distribution in the building interior. First, a 2-D CFD study was conducted to explore various techniques of manipulating the building envelope wind pressure distribution.
Submitted by Maria.Kapsalaki on Wed, 11/06/2013 - 10:02
The importance of adventitious air leakage under normal operational conditions and its reduction in order to save energy is highlighted by the relvant building standards of many countries. This operational leakage is often inferred via the measurement of air permeability, a physical property of a building that indicates the resistance of its fabric to airflow. A building’s permeability is the measure of airflow rate through its envelope at a constant pressure differential of 50 Pascals.
Submitted by Maria.Kapsalaki on Thu, 10/31/2013 - 20:19
The paper presents the whole year simulation of humidity based demand controlled hybrid ventilation in multiapartment building. The simulation was performed for NAPE (National Energy Conservation Agency) multifamily residential reference building. This allowed the authors to compare obtained results with earlier investigated behaviour of the NAPE building with passive stack ventilation and mechanical exhaust ventilation.
Submitted by Maria.Kapsalaki on Mon, 10/28/2013 - 13:58
The importance of reducing adventitious infiltration in order to save energy is highlighted by the relevant building standards of many countries. This operational infiltration is often inferred via the measurement of the air leakage rate at a pressure differential of 50 Pascals. Some building codes, such as the UK’s Standard Assessment Procedure, assume a simple relationship between the air leakage rate and mean infiltration rate during the heating season, the so-called leakage-infiltration ratio, which is scaled to account for the physical and environmental properties of a dwelling. The
Using a passive tracer gas technique, 1 and 2 week averages of local mean ages of air have beenestimated in an occupied detached single family house in mid-Sweden during one year. In this paperthe measurement result is compared with the result of transient simulation of ventilation using theCONTAM program. The simulation shows that the whole-house air change rate is dominated by theinfiltration due to mechanically created pressure difference as long as the outdoor temperaturedifference exceeds approx. 10 C.
A literature search was undertaken to assemble and interpretthe-best available· data that can be used for perfonning multizone airflow modelling in mid and high rise apartment buildings. The best currently available data is presented and areas where further field testing research is required are identified. A multizone airflow modelling software tool was used to provide an analysis of ventilation related energy issues in a newly constructed 10 story high-rise apartment building.